The information presented on this website is informational only and does not necessarily reflect the current condition of the building or property. The fact that a permit was issued does not confirm that work was performed, or that work was performed in accordance with that permit and the requirements of the Municipal Code.
Information on inspections and alleged violations reflect conditions found by the inspector at the time of the inspection and not necessarily the current status of those alleged violations or the current condition of the property. The absence of alleged violations on this website does not mean a building or property is in compliance with the requirements of the Municipal Code.
The Department of Buildings may refer certain alleged violations to the City's Department of Law for enforcement proceedings in the Department of Administrative Hearings or the Circuit Court of Cook County. Please contact the Department of Administrative Hearings or the Clerk of the Circuit Court, respectively to obtain records of these proceedings.
|Inspection # 12628540|
|VIOLATIONS||BUILDING CODE CITATION||VIOLATION DETAILS|
|CN021053||Failed to provide exit door with approved latch or bolt that releases under 15 pounds of pressure in assembly use serving more than 200 persons. (13-160-260(b))||Provide panic hardware at outter front exit doors.|
|CN039013||Failed to post in a conspicuous location, the approved occupancy card indicating the number of people who may legally occupy such rooms and space in every theater, public assembly unit or open air assembly unit and in every room or portion of such units. (13-84-410)||Obtain occupancy cards for Main Gym, Kids Room, Womens Room and Spin Room. and Group X rooms|
|CN061014||Failed to maintain the exterior walls of a building or structure free from holes, breaks, loose or rotting boards or timbers and any other conditions which might admit rain or dampness to the walls. (13-196-530(b), 13-196-641)||Missing sections of sheet metal cladding at south elevation front facade. Loose Mortar an Fractures at Exterior Walls|
|CN061014||Failed to maintain the exterior walls of a building or structure free from holes, breaks, loose or rotting boards or timbers and any other conditions which might admit rain or dampness to the walls. (13-196-530(b), 13-196-641)||Repair miscellaneous fractures and loose mortar at exterior walls.|
|CN070014||Failed to maintain exterior stairways in safe condition and in sound repair. (13-196-570, 13-196-641)||Provide handrail at north exterior stairs.|
|CN073014||Failed to maintain exterior door in sound condition and repair. (13-196-550(d) and (e), 13-196-641)||Northwest exterior door and frame corroded.|
|CN073044||Failed to maintain exterior door hardware in good condition and repair. (13-196-550(d), 13-196-641)||Detached Closer at Northeast Exit door|
|CN074024||Failed to provide porch which is more than two risers high with rails not less than three and one-half feet above the floor of the porch. (13-196-570(b), 13-196-641||Provide guardrail at rear exterior dock|
|CN107025||Failed to install standard internally illuminated exit, fire escape, and/or directional signs. (13-196-090, 13-160-700 thru 13-160-770)||Install exit signs in Womens Room.and Group X room|
|CN197087||Install carbon monoxide detector within 40 feet of every sleeping room in residential structure. (13-64-190, 13-64-210) A carbon monoxide detector is needed whenever there is a heating appliance on the premises that burns fossil fuel such as gas, oil, or coal, or air that is circulated through a heat exchanger. Install according to manufacturer instructions. A hard wired model requires an electrical wiring permit. In a single family residence, be sure the detector is on or below the lowest floor with a place to sleep. In a multiple dwelling residence heated by a boiler, install a detector in the same room as the boiler. Otherwise, each apartment follows single family guidelines. The owner is responsible for installation and written instructions, the tenant for testing, maintenance, and batteries.||Install carbon monoxide detectors at first floor and mezzanine.|
|NC3022||Provide additional means of egress. (13-196-050, 13-160-050)||Provide 36 inch wide gate at rear exterior north fence.|