The information presented on this website is informational only and does not necessarily reflect the current condition of the building or property. The fact that a permit was issued does not confirm that work was performed, or that work was performed in accordance with that permit and the requirements of the Municipal Code.
Information on inspections and alleged violations reflect conditions found by the inspector at the time of the inspection and not necessarily the current status of those alleged violations or the current condition of the property. The absence of alleged violations on this website does not mean a building or property is in compliance with the requirements of the Municipal Code.
The Department of Buildings may refer certain alleged violations to the City's Department of Law for enforcement proceedings in the Department of Administrative Hearings or the Circuit Court of Cook County. Please contact the Department of Administrative Hearings or the Clerk of the Circuit Court, respectively to obtain records of these proceedings.
|Inspection # 13737307|
|VIOLATIONS||BUILDING CODE CITATION||VIOLATION DETAILS|
|CN012022||Failed to construct floor over basement with materials of at least one hour fire resistance, other than in single family and two family dwellings. (13-60-200)||FAILED TO CONSTRUCT FLOOR OVER BASEMENT WITH 1 HOUR FIRE RESISTANT MATERIAL NO DRYWALL @ CEILINGS THROUGHOUT BASEMENT CEILINGS THROUGHOUT|
|CN043013||Failed to enclose pipe shafts and ducts passing from one floor to another with materials providing fire resistance of not less than one hour. (15-8-160)||ALL PIPE PENETRATIONS WHERE PIPE MAY TRAVEL THROUGH FLOORS TO ENTER DIFFERENT SECTIONS OF PROPERTY SHALL BE SEALED WITH FIRE RESISTANT MATERIAL 14X-5-502.3|
|CN101015||Failed to maintain interior walls and ceilings free from holes or cracks. (13-19-540(c))||INTERIOR SURFACE WALLS AT REAR PROPERTY SHOWING SIGNS OF WATER DAMAGES WITHIN OFFICE AREAS AND STORAGE ROOM AREAS BRICK WALL OVER REAR DOOR MARKED EXIT MISSING SECTIONS OF BRICK 14X-3-304.3|
|CN103035||Repair or replace defective structural member. (13-196-530 A)||CURRENTLY BASEMENT HAS TEMPORARY SHORING POST AND BEAM USED AT SECTION OF BASEMENT FOR SHORING OF THE 1ST FLOOR 14X-3-304.3|
|EL1801||Replace defective service. ( 14E-2-230)||1565-89, 1931-57 ENTIRE BUILDING SMALL ELECTRICAL SERVICE ST ALLEY APPEARS TO HAVE DETERIORATED CABLES AT SERVICE HEAD ENSURE ALL ELECTRICAL SERVICE(S) IN APPROVED CONDITION|
|EL1805||Replace defective distribution equipment. (14E-4-408.30, 14E-4-408.36, 14E-4-408.37, 14E-4-408.38, 14E-4-408.39, 14E-4-408.40, 14E-4-408.41) )||1565-89, 1931-57 ENTIRE BUILDING OPEN DAMAGED ELECTRICAL PANEL AT EAST BASEMENT MAINTENANCE ROOM ENSURE DISTRIBUTION EQUIPMENT THROUGHOUT PREMISES IN APPROVED CONDITION DANGEROUS AND HAZARDOUS|
|EL1806||Install proper sized grounding conductor. (14E-2-250.20, 14E-2-250.66)||1565-89, 1931-57 ENTIRE BUILDING NO VISIBLE WATER GROUNDS ENSURE SERVICES(S) GROUNDED IN APPROVED MANNER DANGEROUS AND HAZARDOUS|
|EL1809||Provide at least 3 ft of clear space around electrical service and distribution equipment. (14E-1-110.26)||1565-89, 1931-57 ENTIRE BUILDING CLUTTER,DEBRIS IN FRONT OF ELECTRICAL DISTRIBUTION EQUIPMENT VARIOUS AREAS BASEMENT ENSURE REQUIRED CLEARANCE MAINTAINED THROUGHOUT PREMISES DANGEROUS AND HAZARDOUS|
|EL1816||Install additional receptacle outlets. (14E-5-560.6, 14E-5-570.10(e))||1565-89, 1931-57 ENTIRE BUILDING ADD RECEPTACLES AT BASEMENT AREA TO ELIMINATE EXCESSIVE EXTENSION CORD USE|
|EL1820||Support loose light fixture. (14E-4-410.30, 14E-4-410.36)||1565-89, 1931-57 ENTIRE BUILDING FALLING LIGHT FIXTURES VARIOUS AREAS BASEMENT SECURE WHERE REQUIRED DANGEROUS AND HAZARDOUS|
|EL1823||Install cover on outlet or junction box. (14E-3-314.25)||1565-89 1931-57 ENTIRE BUILDING NUMEROUS OPEN BOXES THROUGHOUT BASEMENT AREAS CLOSE WHERE REQUIRED THROUGHOUT PREMISES DANGEROUS AND HAZARDOUS|
|EL1827||Restore exit and emergency lighting system and related equipment to working condition. (14E-7-700.6)||1565-89, 1931-57 ENTIRE BUILDING INOPERABLE EXIT SIGNS UNAPPROVED EXIT SIGNS INSUFFICIENT BATTERY LIGHTS INOPERABLE BATTERY LIGHTS THROUGHOUT BASEMENT AREA ENSURE REQUIRED EMERGENCY LIGHTING SYSTEM IN APPROVED CONDITION THROUGHOUT PREMISES DANGEROUS AND HAZARDOUS|
|EL1829||Remove exposed wiring. (14E-3-300.4)||1565-89, 1931-57 ENTIRE BUILDING OPEN WIRING VARIOUS LOCATIONS THROUGHOUT BASEMENT AREAS REMOVE WHERE REQUIRED THROUGHOUT PREMISES DANGEROUS AND HAZARDOUS|
|EL1833||Strap and secure raceway and armored cable. (14E-1-110.13(a))||1565-89, 1931-57 ENTIRE BUILDING UNSUPPORTED CONDUITS VARIOUS AREAS THROUGHOUT BASEMENT SECURE WHERE REQUIRED|
|EL1856||Fasten and support outlet and/or junction box. (14E-3-314.23)||1565-89, 1931-57 ENTIRE BUILDING UNSUPPORTED BOXES VARIOUS AREAS THROUGHOUT BASEMENT SECURE WHERE REQUIRED|
|EL1866||Remove unapproved flexible cord. (14E-4-400.12)||1565-89, 1931-57 ENTIRE BUILDING EXCESSIVE CORDS DAMAGED CORDS CORDS THROUGH DOORS VARIOUS AREAS BASEMENT DANGEROUS AND HAZARDOUS|
|EL1886||1565-89, 1931-57 ENTIRE BUILDING PROVIDE ANY REQUIRED ROUGH INSPECTIONS FOR THE INSTALLATION OF ELECTRICAL CONDUIT BOXES WIRE DEVICES AND EQUIPMENT NEW MAIN ELECTRICAL SERVICE INCOMPLETE INSPECTIONS VARIOUS MISCELLANEOUS PERMITS NO INSPECTIONS INCOMPLETE INSPECTIONS (14A-4-404.6)|
|EL1886||1565-89, 1931-57 ENTIRE BUILDING PROVIDE ACCESS TO INSPECT CONDITION OF DISTRIBUTION, ELECTRICAL SYSTEM EMERGENCY LIGHTING SYSTEM THROUGHOUT PREMISES (14A-5-505.2)|
|PL234002||Provide proper soil/waste vent pipe material. (18-29-702)||UNAPPROVED SUSPENDED PVC DRAINAGE PIPING AT BASEMENT SERVING FLOWER SHOP AT 1ST FLOOR 1957 MILWAUKEE|